Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
ION7300 series communications loss when reading registers via Modbus TCP/IP
ION7300 Series Meters (ION7300, ION7330, and ION7350)
The cause of the behavior is the Ethernet stack holding the ports open after a connection has been severed improperly.
As the device believes there is still a connection, it will not accept any incoming requests, and it will hold this state continuously.
The user will lose communications with the meter via Modbus TCP over Ethernet even though the user can still ping the meter.
The only methods of resetting the socket connections are to either power cycle the device or change the meters IP address.
This will clear the Ethernet stack and remove any current broken connections.
In addition, review FA212335 for Ethernet ports and socket summary on ION Meters.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!