Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
User wants to change the logging interval for Powerlogic meters(CM4000, CM3000, PM800, and/or PM600)
CM4000, CM3000, PM800, and/or PM600
Structureware Power Monitoring 7.01
Power Management Expert 7.2.
Meter configuration using ION6.0, SPM, or PME
ION 6.0,Structureware Power Monitoring 7.01, and Power Management Expert 7.2. does not have the capability to change the logging interval for the onboard log files
The onboard logging interval can be changed using ION setup. However, StruxureWare Power Monitoring 7.0, and Power Management Expert 7.2 will not extract Data logs from the meter with an interval at or less than 1 minute. A Work around would be to create data recorders in the VIP which can log data from the Powerlogic meters at intervals of 1 minute or less. Consider the size and complexity of the VIP and system before such configuration.