The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
User wants to change the logging interval for Powerlogic meters(CM4000, CM3000, PM800, and/or PM600)
CM4000, CM3000, PM800, and/or PM600
Structureware Power Monitoring 7.01
Power Management Expert 7.2.
Meter configuration using ION6.0, SPM, or PME
ION 6.0,Structureware Power Monitoring 7.01, and Power Management Expert 7.2. does not have the capability to change the logging interval for the onboard log files
The onboard logging interval can be changed using ION setup. However, StruxureWare Power Monitoring 7.0, and Power Management Expert 7.2 will not extract Data logs from the meter with an interval at or less than 1 minute. A Work around would be to create data recorders in the VIP which can log data from the Powerlogic meters at intervals of 1 minute or less. Consider the size and complexity of the VIP and system before such configuration.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!