The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
G3200 and IEC61850 Client Software: How to detect if the Modbus Slave is Offline to prevent invalid values?
Facts and Changes
Having G3200 Firmware 1.4, PM820 meter connected to G3200 over RS485, some Siemens SCADA (as IEC61850 Client) connected to G3200 on Ethernet port.
If the communication between the G3200 and the PM820 is broken, then the values (last values of the PM820) are still available over the G3200. In this case, would be better to have all PM820 data become invalid. Is there a possibility to change this in the CID file or in the G3200 firmware, or is it impossible?
Causes and Fixes
Current Implementation of G3200 doesn't support updating IEC 61850 database when connected device is Offline.
SCADA connected to G3200 should check the values of LLN0 and LPHD before reading the values. If It finds LLN0.ST.Mod = 5(OFF) then it should not consider reading values from the Modbus device.
This was the G3200 project decision to implement the same functionality as in ECI 850 gateway, so, it is NOT possible to change now.
Please find below the solution for SCADA (or any other IEC61850 Client software) in which we can find if the connected Modbus device is Online or Offline.
LLN0 and LPHD are the two logical nodes dedicated for physical device health and status.
Case1: When connected device is "Online"
LPHD1.ST.PhyHealth = 1(OK)
LLN0.ST.Mod = 1(ON)
Case2: When connected device is "Offline"
LPHD1.ST.PhyHealth = 3(Alarm)
LLN0.ST.Mod = 5(OFF)
G3200 updates IEC 61850 database of the device if and only if device is Online.
Then, it reads the data from device using Modbus and update IEC 61850 database.
If devices gets disconnected, Measures, Quality and Timestamp won't be updated. However, the above mentioned nodes: "LPHD1.ST.PhyHealth" and "LLN0.ST.Mod" should be updated and their values could serve as device status monitoring.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!