The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Webreach or Vista diagrams with orange boxes and it shows 'configuration error'
ION Enterprise, SPM 7.0.1, PME 7.x, PME 8.x
Webreach or vista diagrams is displaying the meter diagram with orange boxes. When hovering over the box, the informational message states "Configuration error"; but Vista is fully functional.
Customer interfacing with Webreach or Vista to see real time readings.
Webreach or Vista Diagrams is displaying the meter diagram with orange boxes. When hovering over the box, the informational message states "Configuration error". Vista is fully functional. This indicates that the device has a special character in the name.
Please verify the device name in Management Console and make sure there is no special character in the name of the devices.
This will most likely occur after a SMS2SPM migration or if the database was manually modified since ION/SPM/PME will not allow a special character through management console.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!