Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
A user wants to use an Enercept meter to monitor a Variable Frequency/speed Drive (VFD), and perhaps on the line side.
Enercept Meter and VFDs
The Enercept meter cannot be used to monitor a Variable Frequency/Speed Drive on the line or load side.
The reason is that, by design, the processor and electrical components are mounted on the current transformer (CT). Any frequency other than 60 Hz, such as harmonics from a VFD, will degrade the electrical components on the CTs.
This has been verified by Veris.
Installation manuals prior to Z205397-0C indicate that it is OK to install the meter on the line side of a VFD. As of January 2011, this is no longer supported for any Enercept Meters regardless of their Date of Manufacture.