The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
The EM4800 configuration tool cannot connect to the EM4800 meter. The following message will be displayed:
"Could not determine unit type based on model number EM48XXXX-3P-08"
The meter will respond to ping commands, and the user can connect to the web server, however the model number listed on the web server will show as "3P-08" model instead of the full part number.
EM4800 configuration tool
In rare cases the meter can lose the model identifier information.
Telnet into the device to manually update the model number information.
Use Windows Command Prompt to telnet the model number to the device.
(Paste or type the following into the command window)
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!