Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Confirming Modbus address and Unit ID
ION Series Meters
Determing Modbus specifications
The Modbus address is dependant on how the meter and communication system is configured
1. If using Modbus TCP, the slave address, the meter default is ID 100. Since all Modbus TCP devices have unique IP addresses it allows the default to be used for all units.
2. If using serial Modbus protocol, the Modbus unit ID is the unit ID of the meter as configured on the relevant serial communication port.
Power PC based ION platforms intorduced the "Modbus Master Options Module" starting with firmware V350. This changes how the meter responds to modus requests:
The default setting is GATEWAY DISABLED, which disables the gateway functionality
and allows the meter to respond to any Unit ID for Modbus TCP (port 502) or
Modbus RTU (port 7701) requests. This is different from the GATEWAY ENABLED setting, which sets the meter to respond only to Unit ID 255 and
enables the gateway functionality even if no downstream devices are setup.
The above statements are excerpted directly from the "Modbus Gateway Connection" subsection of the "Modbus Master Options Module" section of the ION Reference document (p. 386 of 494).