Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The customer sees some value of harmonic on a power meter which is installed at a utility feed. Is there any way determine if this harmonic comes from the utility or it comes from the facility side? In other words, is there any way to determine the direction of the source of the harmonic distortion with the meter?
ION8800, ION8650, ION7650, ION7550, CM4000T, PM8000, PM870, PM850, PM820, PM810, PM800, ION7350, ION7330, PM750, PM710, PM5500, PM5300, PM5100, PM3000
The "direction" of the source of the harmonic distortion is not given directly by the meter itself.
A useful means of detecting whether a customer is imposing harmonics on the system is to look at the relative magnitude of the harmonics, as a percentage of the fundamental voltage and current. If the customer is experiencing harmonics imposed upon him by the utility, then the relative magnitudes of the harmonic current will be less than or equal to the relative magnitude of the harmonic voltage.
For example, if the third voltage harmonic was 3.1% and the third current harmonic was 2.8%, then we would expect that the harmonic current was the result of the harmonic voltage on the utility's line. Since the customer's load is likely to have some reactive (inductive) component which will cause the impedance to be higher for harmonics (making his load act somewhat like a low pass filter), we would expect the current harmonic to be smaller than the voltage harmonic when expressed in percent.
If, however, the reverse is true - the relative magnitude of the current harmonic is greater than that of the voltage harmonic - then the customer's load is probably imposing the harmonic on the utility. This is because the line impedance is likely to be much less than the load impedance, although this effect diminishes at high frequencies as discussed above. Especially at the lower harmonics, this is expected to be true, and it is quite possible, for example, to see a current harmonic of 22% with a voltage harmonic of 3.9%.
Because of resonance, it is possible for occasional harmonics to have exaggerated effects, either reinforcing challenging the conclusion you would draw about who is imposing harmonics on whom. Therefore, you should always look at the harmonics as a group, with special emphasis placed on the first few harmonics (typically the odd ones, say 3rd through 11th) where line impedance effects are likely less exaggerated.
Note: Not all meters are able to provide individual harmonic information.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!