Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
An ION Enterprise 5.6.1 system or greater includes a PM850 or PM870 device. The device reboots periodically for no apparent reason.
ION Enterprise 5.6 Service Pack 1
There is a problem with firmware versions for PM8 devices prior to v10.8 which can cause the device to reboot if it is polled frequently.
Upgrade the meter firmware to version 10.8. Upgrading the meter firmware will also allow the device to provide information required for a CBEMA plot.