Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The ION Reference guide doesn't have an example that explains the transient module and it's operation in detail
ION7550/7650, ION8650(A only)
The following calculations show exactly how the transient module calculates the maximum transient voltage. It is intended to supplement the ION Reference description of this module.
To calculate the magnitude of the first transient, this is the correct process:
In the second transient:
Please note that the predicted normal is based on a series of previous waveforms whereas the nominal value is programmed by the user.
The nominal voltage input is supplied from the sag/swell NomVolts setup register. For a WYE system (3 wire or 4 wire), the nominal voltage must be in terms of Phase-Neutral voltages. For Delta system, the nominal voltage must be in terms of phase-phase.
The default framework is configured such that the sag/swell module will disable the transient module when a disturbance is in progress.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!