The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Energy meter error "bad pulse rate" appears on the front display of a 1600 amp Energy Meter
Pulse Output Selection Availability
The default pulse setting (0.1), is not valid on 1600 A Energy Meter
Change the pulse rate switch setting from 0.1 (default) to a value such as 0.25, 0.5 or 1.0 kWh/Pulse to clear the error.
For more information on Energy Meter Pulse out, refer to article FA260559
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!