Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
What are the phase loss alarm specifications in the Extended Range Energy Meter?
Energy Meter Extended Range (EMExxxx)
User is getting Phase Loss Alarm on energy meter and would like to know what are specification for phase loss alarm
Energy meter is showing Phase Loss alarm on front display
If the voltage of any phase is measured as less than 75% of the voltage on any other phase, the display will show PHASE LOSS and indicate the specific phase(s). The display will not cycle to the other readings and appear locked up. User can still see KWh on right top corner but the display will not rotate through other readings.
NOTE: If user verifies there is sufficient voltage provided to energy meter and the display still shows PHASE LOSS alarm, then review KB FA203758.