Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
|If this error occurs while connected serially, make sure the protocol mode is PowerLogic and the parity is EVEN.
Modbus mode or Parity NONE will not work over a serial connection.
If this error occurs while connected over ethernet, make sure that there are no ION or SMS services communicating with the device.
With SMS, make sure SMS is not constantly polling, logging, or uploading.
With ION Enterprise or PME, stop the ION Network router service before sending firmware to the meter.
All content © 1992-2007 Schneider Electric