Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
A user would like to set the address and baud rate on a CM100/200 series meter
CM100/200 series meter
Baud rate and device address parameters are required to communicate with the meter
|1) Disconnect control power from the unit
2) Set the 2 rotary selector dials to the correct setting for the baud rate (97=9600).
3) Restore power
4) Wait 5 seconds, disconnect power again
5) Set the 2 dials to the desired address (Range includes 1 to 32)
6) Restore power.