Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
A user would like to set the address and baud rate on a CM100/200 series meter
CM100/200 series meter
Baud rate and device address parameters are required to communicate with the meter
|1) Disconnect control power from the unit
2) Set the 2 rotary selector dials to the correct setting for the baud rate (97=9600).
3) Restore power
4) Wait 5 seconds, disconnect power again
5) Set the 2 dials to the desired address (Range includes 1 to 32)
6) Restore power.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!