The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
If an SMS system is experiencing frequent communications loss alarms, the user may not want to be alerted with an audible or flashing alarm.
System Manager Software
An SMS system with the default alarms severity that has frequent communications loss alarms.
The communications loss severity is set to 1. This severity is associated with flashing red text and an audible alarm.
Go to the SMS Configuration under the Diagnostics Tab you will see a setting for Comms Loss Alarm Level. You can select levels 0-9 here which corresponds with the settings for PC Based Alarms 0-9.
After selecting the desired level, close the SMS setup utility and restart the SMS services to apply the changes.
Note: The behavior that each severity level has can be viewed and configured in the SMS Setup Utility under Setup>Functions and Alarms>Global Functions. Highlight any function and select "Setpoints>>". From here, click "Severity". This is the global severity behavior for all functions and alarms.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!