Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
If an SMS system is experiencing frequent communications loss alarms, the user may not want to be alerted with an audible or flashing alarm.
System Manager Software
An SMS system with the default alarms severity that has frequent communications loss alarms.
The communications loss severity is set to 1. This severity is associated with flashing red text and an audible alarm.
Go to the SMS Configuration under the Diagnostics Tab you will see a setting for Comms Loss Alarm Level. You can select levels 0-9 here which corresponds with the settings for PC Based Alarms 0-9.
After selecting the desired level, close the SMS setup utility and restart the SMS services to apply the changes.
Note: The behavior that each severity level has can be viewed and configured in the SMS Setup Utility under Setup>Functions and Alarms>Global Functions. Highlight any function and select "Setpoints>>". From here, click "Severity". This is the global severity behavior for all functions and alarms.