Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Yes, it is possible to establish a programming connection via TCP IP to the ETY modules or the Integrated PORT on some processors.
Programming via TCP IP requires the installation and configuration of the XIP Driver.
Programming via Ethway is also possible for the ETY110 only.
These Drivers are supplied on the XWAY Driver CD - TLXCDDRV13M
The ETY Module must be configured with a TCP/IP and Xway address prior to being able to establishing a programming connection with the XIP Driver.
The initial configuration should be performed via the Unitelway driver connected to the processor TER port.