Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The following table provides power supply information for the Modular controller.
|Power supply voltage||Rated power voltage; 24 vdc |
Allowable range; 20.4 to 26.4 vdc
Failure depends on quantity of used inputs and output points. Generally, failure is detected when voltage drops below 20.4 vdc, stopping operation to prevent malfunction.
|Inrush current flow at power-up||50 Amps maximum|
|Power supply wiring||UL1015 AWG22 (0.64 mm) or UL1007 AWG18 (1.02 mm) |
Make the power supply wiring as short as possible.
|Ground wiring||UL1015 AWG22 (0.64 mm) or UL1007 AWG18 (1.02 mm) |
Do not connect ground wire in common with ground wire of motor EQUIPMENT.