Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
The following table provides power supply information for the Modular controller.
|Power supply voltage||Rated power voltage; 24 vdc
Allowable range; 20.4 to 26.4 vdc
Failure depends on quantity of used inputs and output points. Generally, failure is detected when voltage drops below 20.4 vdc, stopping operation to prevent malfunction.
|Inrush current flow at power-up||50 Amps maximum|
|Power supply wiring||UL1015 AWG22 (0.64 mm) or UL1007 AWG18 (1.02 mm)
Make the power supply wiring as short as possible.
|Ground wiring||UL1015 AWG22 (0.64 mm) or UL1007 AWG18 (1.02 mm)
Do not connect ground wire in common with ground wire of motor EQUIPMENT.