Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The following table provides power supply information for the Compact controller.
|Power supply voltage||Rated power voltage; 100 to 240 vac.
Allowable range; 85 to 264 vac.
Failure - depends on quantity of used inputs and output points. Generally, failure is detected when voltage drops below 85 vac, stopping operation to prevent malfunction.
NOTE: Momentary power interruption for 20 ms or less at 100 to 240 vac is not recognized as a failure.
|Inrush current flow at power-up||TWDLCAA10DRF and TWDLCAA16DRF 35 Amp maximum
TWDLCAA24DRF 40 Amps maximum
|Power supply wiring||UL1015 AWG22 (0.64 mm) or UL1007 AWG18 (1.02mm) Make the power supply wiring as short as possible.|
|Ground wiring||UL1007 AWG16 (1.30 mm) Do not connect ground wire in common with ground wore of motor EQUIPMENT.|