Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
The following table provides power supply information for the Compact controller.
|Power supply voltage||Rated power voltage; 100 to 240 vac.
Allowable range; 85 to 264 vac.
Failure - depends on quantity of used inputs and output points. Generally, failure is detected when voltage drops below 85 vac, stopping operation to prevent malfunction.
NOTE: Momentary power interruption for 20 ms or less at 100 to 240 vac is not recognized as a failure.
|Inrush current flow at power-up||TWDLCAA10DRF and TWDLCAA16DRF 35 Amp maximum
TWDLCAA24DRF 40 Amps maximum
|Power supply wiring||UL1015 AWG22 (0.64 mm) or UL1007 AWG18 (1.02mm) Make the power supply wiring as short as possible.|
|Ground wiring||UL1007 AWG16 (1.30 mm) Do not connect ground wire in common with ground wore of motor EQUIPMENT.|