Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
This is possibly due to the fact that the word order for the slave device differs from the PLC. Try swapping the word order after the value is read in at the M340. If you are reading the value into %MW0, the REAL number occupies %MW0 and %MW1 as a 32 bit REAL number. You can do something like %MW100:=%MW1;, %MW101:=%MW0;. Now create a Variable located to %MW100 of datatype REAL and see if the number is displayed properly.