The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Yes, this can be done using the Offset References command in Concept. This must be done offline.
With a 984LL section open in Concept, go to the menu <Edit> <Offset References>.
You will need to know how many references are configured. 0X, 1X, 3X and 4X (PLC Configurator)..
Enter the first 0X reference in 'First Reference' column of the first line, followed by 'Last Reference'.
Do this for the 0X, 1X, 3X and 4X references.
IMPORTANT: The Offset Inc column must be filled in on each entry. Enter '0'.
Click on <Sections> and choose the 984LL sections that you want to link to the variables.
Check <Substitute variables if they exist> and hit <Offset>.
You should see a status box telling you how many references have been changed.
When viewing the 984LL section, you must be in Expanded view <View>.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!