Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Xxmit Error code 120 - could not set PLC UART
Causes and Fixes
The most common cause of XMIT / XXMIT error 120 "XXMIT Could Not Set PLC UART" is trying to access a Modbus port that doesn't exist. Since you have a TSX Momentum 171CCC78010 which has 2 Modbus ports, the second most common cause of error 120 "XXMIT Could Not Set PLC UART", it trying to set 2 Stop Bits in a TSX Momentum. The UART that's used for the TSX Momentum Modbus port is not capable of 2 Stop Bits (only 1).