The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Xxmit Error code 120 - could not set PLC UART
Causes and Fixes
The most common cause of XMIT / XXMIT error 120 "XXMIT Could Not Set PLC UART" is trying to access a Modbus port that doesn't exist. Since you have a TSX Momentum 171CCC78010 which has 2 Modbus ports, the second most common cause of error 120 "XXMIT Could Not Set PLC UART", it trying to set 2 Stop Bits in a TSX Momentum. The UART that's used for the TSX Momentum Modbus port is not capable of 2 Stop Bits (only 1).
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!