Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
A Proworx 32 project, for example, has an IO map configured with an NOM, two NOEs and an RIO module.
PLC (DIO 1) = Slot 2
NOM (DIO 2) = Slot 4
NOE(1) = Slot 5
NOE(2) = Slot 10
CRP = Slot 16
Once the project is imported into Unity Pro, the Configuration as below in the the Unity Project Browser.
Local Bus = Bus 1
DIO Bus = Bus 2
RIO Bus = Bus 5
Here is how these numbers are assigned and why there are only 3 Buses.
The numbers are assigned in sequence for network interfaces.
The only buses that are shown in the configuration are Local, DIO configured for Peer Cop, and RIO.
Bus 1 is assigned to the CPU in slot 2,
Bus 2 is assigned to the NOM in slot 4 because it is configured for Peer Cop,
Bus 5 is assigned to the CRP RI/O head located in slot 16.
Bus 3 and 4 that are not seen because they are allocated to the NOE's in slots 5 and 10.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!