Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Can I read simple ASCII characters into my Quantum PLC via a Network Option Ethernet module (140NOEXXXXX)?
Causes and Fixes
No. The quantum Network Option Ethernet modules (140NOEXXXXX) can only accept Modbus TCP/IP messaging. They cannot read in ASCII characters. ASCII messaging can be accomplished either via the 140ESI06210 ASCII interface module or via the XMIT (984LL) or XXMIT(IEC) instruction from Modbus port #1 on the CPU module.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!