The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
What could cause a red I/O fault on the QEIO Drop 140CRA31200 card?
Causes and Fixes
There are three reasons why you would get a red I/O fault LED on the 140CRA31200 drop card while getting a solid green LED on (RUN, Mod Status and Net Status):
1) Defective I/O module.. No Active LED (See Note#2 below - External error is detected).
2) I/O Module is missing from Unity project drop I/O map.
3) I/O Modules is in the wrong drop I/O map location.
The LEDs on the front of the adapter module:
140 CRA 312 00:
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!