Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
No, the STBACI1400 will not work with the STBAHI8321KC module. It is not Hart tolerant; the grounding is single ended and there is no impedance adaptation with the STBAHI8321KC. The channels are not isolated and any Hart signal will corrupt the 4-20 mA signal. The recommended ACI modules are the STBACI0320 and the STBACI8320 to be used with the STBAHI8321KC.