Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
No, the STBACI1400 will not work with the STBAHI8321KC module. It is not Hart tolerant; the grounding is single ended and there is no impedance adaptation with the STBAHI8321KC. The channels are not isolated and any Hart signal will corrupt the 4-20 mA signal. The recommended ACI modules are the STBACI0320 and the STBACI8320 to be used with the STBAHI8321KC.