Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
This error can be seen if there was an interruption to the Executive Flash process. Sometimes the PLC is recoverable and sometimes it is not. To recover, some of the actions listed below can be attempted. Remove any PC cards installed in the PLC and any cards other than the PLC and PS from the back plane. If available, try a different power supply and back plane.