Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Error 100 means that in the 4th register of the MsgOut pin (Slave PLC Data area) has a zero. This is probably a timing issue with the multiplexing logic.
Error 150 means that one XXMIT still has the comm port while another XXMIT is attempting to access it (comm port not available). This is also probably a multiplexing issue.
Suggested method of troubleshooting is to disable all but one XXMIT and test them each individually in this manner. If they function independently, you must revisit logic and ensure that only one block can be fired at a time. If you are multiplexing values into the XXMIT blocks, ensure that the values are present before enabling the block.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!