The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
To show how to have more than one Drum sequence running at the same time. See attached file for a running demo of 2 Drum sequences running at the same time.
Causes and Fixes
When running more than 1 drum sequencer in a program at the same time it is required that you do not use the same registers in both. The below is showing a %DR0 and a %DR1. %DR0 is using the %Q reference using 8 bits for each sequence.
%DR1 is using %M reference using 8 bits for each sequence
(Removed File URL: 211560_4FEA/Drum.xar)(Removed Image URL: /PubResEXPORT.nsf/2b87ee90be777fc085257c28006ee4ef/74750d444d8b3253c1257b75005a405d/fl_block_5/0.C4?OpenElement&FieldElemFormat=gif)
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!