Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
An error number 19002 is a slot error. 190EE where EE points to the slot number experiencing the error so 19002 points to slot number 2. POSSIBLE CAUSES below:
1) Improper rack addressing in which remote drops are assigned to a slot which contains a LI or LTI card.
2) Improper seating of module in rack, edge connector of module may be damaged or the rack or slot has been damaged.