The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
No, you do not need to supply a 24vdc connection to 1L+. Signal 1L+ is located on Row 1, terminals 11 and 12 and Row 2, terminals 1 to 8, all of which are internally connected. The 170ARM37030 will provide a 24vdc output for use with the 24vdc field input devices. This 24vdc source is derived from the 120vac module power and provides up to a maximum of 100ma @24vdc. An optional external 24vdc power supply can also be used to power the field side input devices.When using an external 24vdc source, its return or common must be connected to Row 1, terminals 13 or 14 (M-)
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!