Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
To inform users of the reason for not being able to read 2000 Coils from a Premium ETY_Port, ETY4103 or 5103
Facts and Changes
Users attempting to read a large number of coils(1000+) from a Premium PLC through an ETY_Port, ETY4103 or 5103 will encounter an Exception Response 2 ( Illegal Data Address).
Causes and Fixes
This limitation is due to the fact that on Premium the Modbus requests are mapped on UNITE requests on the back plane. These UNITE request access the the data as Booleans. As each Boolean in Premium takes several bits (one for the value, one to indicate if it is forced or not, ....) and as UNITE requests are limited in term of size, this leads to the limitation of 1072 bits.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!