Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The most common reasons for this problem are as follows:
1. When using 24vdc encoders with single ended signals, broken wire detection for the counter input(s) must be disabled in order for the counter output(s) to function. This is done by setting bit 7 (signal LE_D) of configuration output word 3 (for counter 1) or output word 4 (for counter 2) to a one.
2. The 170AEC92000 module should have a minimum SV (software version) of 1.03. This information can be found on the label, typically on the rear of the I/O base. As this firmware version can not be upgraded in the field, the module will have to be exchanged.