Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Using Advantys Configuration software to connect online to an Advantys STB Network interface module (NIM) via the MB programming port causes an error. The Advantys configuration software (ACS) will utilize the Modbus driver, which will be installed during installation of ACS, if one does not exist as part of any Schneider Electric programming software already installed.
Facts and Changes
Advantys Configuration software v 4.7
Causes and Fixes
This error would typically indicate one of two things, either the MB driver is conflicting with another vendors driver or that the MB driver is not running at all. Therefore, do the following to start the driver:
Go to Start > Programs > Schneider Electric > Communication Drivers > MODBUS Driver. Now an icon should appear in the system tray showing that the MB driver is running.