Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
How can I set a T function on relay RE11RMXMU?
Customer wants to use bistable relay function which is marked as Tl function. On the product the switch to the position Tl/Tt and connect the Y1 contact in order to control this function but he claims that there is no possibility to set infinite value on time range.
According functional diagram for bistable relay function the time between two pulses is infinite. But the relay all the time starts to count the delay according the position of potentiometers (time range and time unit).
How is possible to get infinite time between two pulses generated by Y1 contact?
Facts and Changes
Causes and Fixes
You have to select the range selector 10-100h and adjust the unit potentiometer at maximum => 10, then the time is infinite between two pulses on Y1.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!