Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Don’t miss the latest events, videos, or articles. It’s all in our news bulletin.Sign up now
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Partial reads cannot be performed from a 984-xxx non E PLC
Facts and Changes
'ProwORX 32 version 2.1, SP1A
Causes and Fixes
If you try to perform a partial read from a non E 984 PLC (i.e., 984-685, 984-785, etc.) the options for
configuration and logic will be greyed out.
The reason a partial read cannot be performed from a non-E controller is because when the upload
is performed, the configuration automatically gets wiped out from the offline program and replaced with
the uploaded one (Modsoft asks if the user wants to continue before wiping out the configuration).
'ProWORX 32' automatically assumes that the user wants to wipe out the configuration. When this
happens, it causes a mismatch between the offline program and the program that is in the PLC and greys
out the selections.