Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
CANOPEN run light never stops blinking when the address is correctly assigned to the NCO2212
Facts and Changes
Causes and Fixes
When you insert an Advantys island as a slave in the 'Sycon' software, only the first four (4) RxPDO's
and TxPDO's are enabled.
If you enable any of the other 'PDO's', the COB-ID's that Sycon assigns to 'TxPDO 5' through 'TxPDO xxx'
(i.e., TxPDO 12, etc.) or 'RxPDO 5' through 'RxPDO xx (i.e., RxPDO 12, etc.) could be outside of the range
specified by the DS301 version 4.02 'CANopen Application Layer and Communication Profile'
specification. If this happens, the CANOPEN run light on the NCO2212 will stay blinking even if
the correct CANOPEN network address is configured for the module.
The following table is from the 'CANopen Application Layer and Communication Profile' specification
DS301 version 4.02.
To resolve the problem: