Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Please inform me about the right voltage level and type (AC or DC) of the probe of RM35LM33MW relay (2007 Zelio Control catalogue page 56)! I see it is 12V, but it is not determined whether it is AC or DC.
Causes and Fixes
DC voltage would create an electrolysis in the liquid to detect.
The voltage of the probe terminal is 12V AC 500Hz. The frequency is design to optimize the detection in all conditions, without being perturbated by EMC
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!