The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The function block AVGMV doesnt operate correctly if all the following 3 conditions are true:
1. The project has been created under Concept 2.2 SR1 or SR2 AND contains at least
one function block AVMGV.
2. The project has been directly imported to Concept 2.6 SR4 or higher
(without importing first to Concept 2.5 SR1/SR2 or Concept 2.6 SR1/SR2/SR3)
3. The AVGMV input N gets values greater than 50
In this case parts of the subsequent user logic will be overwritten. The resulting events are not predictable (e.g. incorrect operating of the user logic, CPU crash, )
Causes and Fixes
How to detect and to fix the issue if the application contains AVGMV function blocks:
1. Copy the attached AVGMV.exe into a separate (empty) folder.
2. Run the AVGMV.exe. This will introduce the folder AVGMV and the subfolders
BIN, LOG and OUTPUT.
3. Export all the projects containing at least one AVGMV using the Concept Converter.
Use the Menu "File/Export/Project with used DFBs",
This will create the export files "project.asc".
Important: Do not use the Menu "File/Export/Project with used DFBs (Re-Connect to EQUAL)".
4. Copy all the exported Concept projects (ASC files) into folder AVGMV.
5. Click on file AVGMV\BIN\do.bat (this will start the tool).
6. When ready, all the projects which have been affected are repaired and are gathered in
the subfolder OUTPUT.
The original versions of the project files (not repaired) remain in the folder AVGMV.
The projects which are saved in subfolder OUTPUT are affected and must be downloaded to the PLC.
A log file has been created in subfolder LOG, it will list the affected projects.
Not affected projects do not appear in the subfolder OUTPUT and remain untouched in the folder AVGMV.
7. Import all the ASC files from OUTPUT folder using the Concept Converter and download
the application to the PLC.
(Removed File URL: 199831_C9EE/avgmv.exe)(Removed Image URL: /PubResEXPORT.nsf/2b87ee90be777fc085257c28006ee4ef/4b46ebca0c318918c1257624003cac5f/fl_block_5/0.540?OpenElement&FieldElemFormat=gif)
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!