The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Discuss the requirements for making an on the fly configuration change (CCOTF) to a Unity HSBY system.
Facts and Changes
Unity 4.1 offers a client the ability to make "I/O Map" changes to a running HSBY system. Changes are restricted to the I/O Map of an existing RIO drop.
Modules may be added, removed or have changes made to the Module Parameter screens in any previously configured drop. You cannot add a new RIO drop or expand the CPU configuration size where %M,%I,%IW,%MW is concerned.
Causes and Fixes
There are minimum requirements which must be met in order to take advantage of this feature. 1: You must be a Unity 4.1 user. 2: The CPU 67160 and its Ethernet coprocessor must use OS version 2.70 or later. * 3: The CRP93x 00 and CRA93x 00 must use OS version 2.00 or later. * 4: The user must select the "Online modifications in run" option during CPU 67160 configuration. * This firmware is available on the Unity OS 2.70 CD
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!