Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
To determine the heat dissipation of a Magelis XBT-GT5230 based on the VA rating of the unit.
Facts and Changes
-1 Watt equals to 3.412 BTU/Hr.
-Power Factor of the Magelis XBT-GT5230 is almost one. But for heat dissipation calculation we will use 0.8
XBT-GT5230 Power Consumption: 26VA
Causes and Fixes
To calculate the heat dissipation you need to consider the type of load you are dealing with. Typically if you have a capacitive or inductive load, you would need to know the power factor (PF) to convert to Watts. :
Watts = VA * PF
VA = Watts/PF
VA = 26/0.8 = 32
32 Watts is about 110 BTU/hr.
Therefore the heat dissipation on a Magelis XBT-GT5230 is 110 BTU/hr. Please choose an electrical enclosure accordingly.