The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Concept 2.6 - During Download Changes the PLC sporadically stops with StopCode 0004 (Logic CheckSum Error)
The problem might occur if the 140CPUx341x A EXEC rev 1.40 or 140CPU53414 B EXEC rev 1.12
are used in the application and the PLC Memory Defragmentation is activated.
Facts and Changes
Reason: In some cases the Defragmentation changes administration data without changing
This problem does not occur with
140CPUx341x A EXEC rev 1.39 and lower
140CPU53414 B EXEC rev 1.11 and lower
Causes and Fixes
The problem will be fixed with
140CPUx341x A EXEC rev 1.41
140CPU53414 B EXEC rev 1.13
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!