The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The purpose of this Resolution is to inform users of Advantys STB Ethernet/IP NIMs of a communications problem between the STBNIC2212 and an Allen-Bradley ControlLogix 1756-ENET/B bridge.
Facts and Changes
The latest A-B bridge, 1756-ENBT/A, will successfully communicate with the STBNIC2212.
Although the 1756-ENBT/A bridge is a direct replacement for the older 1756-ENET/B bridge, the NIC2212 does NOT work with the older ENET/B bridge.
Causes and Fixes
There are no plans to correct the issue that occurs between the STBNIC2212 and the older ENET/B version. The Allen-Bradley 1756 - ENBT/A must be used.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!