Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Hardware Catalog Manager does not import PDO mapping for 'Advantys analog IO modules
Facts and Changes
All versions of Unity
Causes and Fixes
If you import an Advantys exported EDS file into a Unity 'M340' application using the 'Add Device'
feature, the information for the analog I/O modules do not get imported.
The reason that some of the IO modules may not get imported is because the number of IO modules
that can be imported by the software is limited per the CAN open specification. To resolve the issue,
the missing PDO's and TDO's for the IO devices must be added into the Advantys configuration
manually before exporting to a '.eds' file.
For further explanation on why the problem occurs and how to resolve it, reference resolution (193001)
(Removed File URL: 198226_B64A/Cannot_see_the_PDO's_for_FTM_analog_modules_in_the_IO_image_Overview.zip)(Removed Image URL: /PubResEXPORT.nsf/2b87ee90be777fc085257c28006ee4ef/200e3e3cf277a64ac12577540052af76/fl_block_5/0.646?OpenElement&FieldElemFormat=gif)