Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
How do you change the port parameters of the Modbus configuration (CFG) port of an Advantys STB network interface module (NIM)
Facts and Changes
Advantys Configuration Software
Causes and Fixes
This would be an online function utilizing the Advantys Configuration software. First, connect to the NIM with the Advantys Configuration software via the MB (CFG) port or Ethernet port in the case of the STBNIP2212. Once connected, go to the Online menu and select Configuration Port Settings. Now you can modify the port settings including Modbus Node ID, Baud Rate, and other communication parameters. Selecting OK will then prompt you that you will be disconnected and need to confirm. Once confirmed, you will be disconnected and your new port settings will be established. Now you can reconnect to the MB (CFG) port via the new port settings.