Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
The TSXETC100 cannot scan a Allen Bradley Control Logix PLC. The reason for this is because of a proprietary way of peer to peer communication between Allen Bradley controllers. They use Produce and Consume tag in order to synchronize information between PLCs and do not have an assembly object that the TSXETC100 can scan.
Note: The TSXETC100 can be an adapter to a Allen Bradley controller so the Control Logix PLC can scan the TSXETC100.