Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
Modbus error 161 gets returned when trying to connect to a Modicon PLC with 'ProWORX 32'
Facts and Changes
'ProWORX 32', 'ProWORX NxT', 'Modsoft' and 'Concept'.
Causes and Fixes
'Modbus error 161' is defined as an invalid address or address range.
To resolve the problem:
1.) Check the address and communications parameter setup to ensure that they are correct.
2.) Check the Modbus cable to see if the DSR connection is asserted high.
3.) Try placing the PLC into Dim Awareness and use the 'PLC & I/IO Status' function in Modsoft to
view the status. (If this is succcessful, download to the PLC using the default parameters of
(Modbus address, RTU, 8, Even, 1, 9600).