Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Schneider Electric Global Website×
Explore our global offerings or select your country from one of our five regions.Global
Découvrez nos offres globales ou sélectionnez votre pays dans l’une de nos cinq régions.
Goals and Symptoms
You Open the .STU file and get the error message 'Error when opening the project file'.
Facts and Changes
UnityPro V4.0 or older.
Causes and Fixes
This error happens, if in the NOM configuration the communication type 'DIO Bus' is marked, but no DIO drops are configured. The problem is fixed with UnityPro V4.1. In older UnityPro versions you should avoid a marked 'DIO Bus' without DIO drops configured.