The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
This Resolution describes the problem and solution if users experience XXMIT Status Error 150.
Facts and Changes
The XXMIT function block intermittently faults with a status error 150 if the M1 PLC is power cycled when the XXMIT block is still active. This problem may occur with either M1 or M1E processors and will only occur with IEC Execs installed. It will not occur if 984LL Execs are installed.
Causes and Fixes
To resolve this problem, update the IEC Exec to version 2.11 or higher for M1 processors. For M1E processors, update the M1E IEC Exec to 1.30e or higher.
M1 Processor part numbers capable of supporting IEC Execs: 171CCS76000, 171CCC76010, and 171CCC78010.
M1E Processor part numbers capable of supporting IEC Execs: 171CCC96030 and 171CCC98030.
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!