The Internet of Things (IIoT) offers unprecedented possibilities for industries. Stay ahead with EcoStruxure™ Plant and Machine.Learn more
...with the EcoStruxure™ Facility Expert (formerly known as Facility Hero) app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
The story behind the Shedd Aquarium, a smart, sustainable facility that connects people to animals, with EcoStruxure™.Discover how
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
The EXECs rev 2.43 and 2.44 for the Quantum CPU 113 02 / CPU 113 03 / CPU 213 04 (q186v243.bin, q186v244.bin)
Facts and Changes
The bug results in wrong time behavior of:
- System functions like Online PLC scan time and the application watch dog timer.
- All time dependent IEC-EFBs like TON, TOF, FREERUN, SYSCLOCK etc.
- All time dependent LL984-Instructions like T.01, T0.1, T1.0, PCFL etc.
Causes and Fixes
Use EXEC rev 2.45 (q186v245.bin or q1sv245E.bin) or higherThe EXEC s also are available on www.telemecanique.com
Sign up for all the latest solutions, offers and best practices straight to your inbox.
We are excited that you have joined the group. You will receive your welcome email soon describing the program and what to expect in the upcoming weeks. Enjoy!