Here’s what more than 2,500 business decision-makers around the world say.Download the report
...with the Facility Hero app in hand! Discover how you can optimize your maintenance efforts today.Learn more
Access tailored services, 24/7 self-service and expert help. Anywhere, anytime, any project.Discover now
Everything you need to know about our IoT technology backbone.Learn more
Welcome to the Schneider Electric Global Website×
Goals and Symptoms
Search for a register only finds the coils used in the logic.
Facts and Changes
ProWORX 32 version 2.1B
Causes and Fixes
If you set the number for the 'End' parameter of the 'Network Range' in the 'Search' window to anything
greater than 5000 (i.e., 9999), location results for only the coils will be found. It does not return any location
results for the contacts. This only happens when the project is connected to the PLC in either the Online or
Combined mode. In some cases, the opposite behaviour may occur where only one of the contact
location will be found.
To resolve the problem, use a number that is less than 5000.